TYY YF-1 Fire Alarm Control Panel
Prevent sending false alarms through TYY YF-1 Fire Alarm Control Panel complete with a two-stage alarm delay function. The first signal that is sent will reset the signal and the panel will enter 8 seconds standby. At the second stage, if another signal is detected within 9 to 40 seconds, the panel will finally alert the fire alarms.
Identify general zones of fire threat and experience world-class fire protection with TYY’s conventional fire alarm system. From manual call point to control panel, each TYY device offers efficient fire detection and alarm solution across defined areas best suited for smaller properties and businesses.
Stand-by Battery Protection System
During power outages, the built-in battery will automatically stop discharging to extend battery life.
The control panel switches and all the base board components of this unit are all certified by CNS and CE.
All circuit boards use a modular design. The external lines are also separated from the terminal circuit board with protections implemented on the input end. If a faulty power supply is connected to the circuit board caused fault, only the affected circuit board needs to be removed without disconnecting the external lines improving maintenance and inspection efficiency.
This unit’s circuit display uses high-end heat-resistant plastic. With the circuits designed with indication plates, it makes all information regarding the buildings, floors, and circuit properties clear at a glance.
This Central Control can be integrated with other safety and security systems to create a comprehensive system for efficient evacuation assistance during fire emergencies.
|Power Supply(AC)||AC 220V 50 / 60Hz|
|Backup Power Supply||DC 24V|
|Charging Voltage and Current||Under DC26V 450mA , fixed voltage trickle charging|
|Circuit External Impedance||Circuit impedance 50Ω or less, impedance to ground 2MΩ or more|
|Detector Installation|| No limitation for the number of Conventional Rate of Rise Heat Detectors / Fixed Temperature Heat Detectors.
A maximum of 30 smoke detectors (DC24V 40μA) can be connected to a loop.
|Number of Indicating Lamp||1.2 times of the panel loop (LED indicator light)|
|Number of Fire Alarm Bell||1.2 times of the panel loop|
|Cabinet Material||Steel plate with powder coating|
|Main Sounder||Monotone buzzer (over 85dB at 1 meter away)|
|Alarm Relay Contact||Non-voltage NO contact capacity AC250V 7A × 2 sets|
|Panel Color||Red / Green|